Complete Renovation of Vasant Dada Patil Sugar (VDPSSK) 17 MW Steam Turbine Boiler including 132 KV Switch Yard and Substation for Co-Gen Power Plant Nashik (On Going). Accredited by Ministry Of New & Renewable energy.
Complete Diagnostic and Monitoring of 40 MW Quingdao Chinese Turbine of Bengal Energy which was not being able to be loaded over 18 MW. Detailed monitoring revealed HP turbine catenary issue coupled with improper thermal gradient across the stages within turbine cylinder due to low inlet steam temp and heaters remaining out of service for long. The unit was rectified and loaded to full load.
Annual Maintenance Contract at 30 MW Power Plant for Adhunik Alloys at Jamshedpur, Jharkhand.
Complete Revamp of 17 MW Hanzhao Make China Turbine Generator for Kohinoor Jamshedpur.
Outage management for 270 MW Turbine Generators at Jindal Stainless.
Long Term Support to services for Start Up Diagnostics for Ansaldo in India.